sku: PD6363-7R7 Product Type: 1/8 DIN Dual Input Flow Rate/Totalizer Digital Panel Meter Input: Dual Inputs, Pulse Output Options: 4 Relays & 4-20 mA Output Power: 12-24 VDC/VAC Approvals: CE, UL/C-UL Transmitter Power: 5 or 10 VDC @ 50 mA or 24 VDC @ 100 mA + 24 VDC @ 40 mA Display Category: LED, Dual Line Display: 0.6″ High, Dual Line, 6 Digits, Red LED Warranty: 3 years Product Series: ProVu Product Family: PD6363 Product category: Digital Panel Meters Product Application: Flow Rate Totalizer, Speed
The PD6363 is a member of the ProVu series of 1/8 DIN digital panel meters that is specifically designed to display flow rate and total from two (2) pulse output (NPN, PNP, TTL, switch contact, sine wave, etc.) flowmeters. It displays these signals on a dual-line, 6-digit display that is available with optional Sunbright® sunlight readable LEDs. The dual-line display can be used to show both flow rates simultaneously, to alternate between the two inputs showing both the flow rate and total of each, or to show the result of math functions performed on the flow rates and totals. Like all ProVu meters, the PD6363 includes UL / C-UL listing and CE marking, a NEMA 4X front, and AC or DC power options. ProVu meters can be equipped with up to four internal relays, a 4-20 mA output, and Modbus® RTU serial communications. The PD6363 dual-input flow rate/totalizer includes a 24 VDC power supply to drive the flowmeter and can be programmed via the front panel pushbuttons or free MeterView® Pro software.
Display: Upper display: 0.60″ (15 mm) high. Lower display: 0.46″ (12 mm) high. 6 digits each (-99999 to 999999), red LEDs with lead zero blanking. Display Intensity: Eight user selectable intensity levels Display Update Rate:(PD6262): 5/second (200 ms) (PD6363): Rate: 10 per second; up to 1 per 100 seconds (and is a function of Low Gate setting); Total: 10 per second (fixed) Overrange: Display flashes 999999 Underrange: Display flashes -99999 Display Assignment: The Upper and Lower displays may be assigned to show: One or more rate channels: Channel A (Ch-A), B (Ch-B), or C (Ch-C), Toggle between rate channels: Ch-A & Ch-B, Ch-A & Ch-C, Ch-B & Ch-C, and Ch-A, Ch-B, & Ch-C, Total or grand total: Ch-A or Ch-B, Rate and total or grand total: Ch-A, Ch-B, Relay set points, Max and/or min values: Ch-A, Ch-B, or Ch-C, Toggle between any rate channel & units, Toggle between any rate/math channel & units, Total and units: Ch-A or Ch-B, Toggle between totals: Ch-A & Ch-B; Ch-A, Ch-B, and sum of Ch-A and Ch-B, Modbus input. The lower display may also be set to show engineering units or be off, with no display. Programming Methods: Four front panel buttons, digital inputs, PC and MeterView Pro software, Modbus registers Max/Min Display: Max/min readings reached by the process are stored until reset by the user or until power to the meter is cycled. Password: Three programmable passwords restrict modification of programmed settings and two prevent resetting the totals. Pass 1: Allows use of function keys and digital inputs Pass 2: Allows use of function keys, digital inputs and editing set/reset points Pass 3: Restricts all programming, function keys, and digital inputs. Total: Prevents resetting the total manually Gtotal: Prevents resetting the grand total manually Noise Filter:(PD6262) Programmable from 2 to 199 (0 will disable filter) Filter Bypass:(PD6262) Programmable from 0.1 to 99.9% of calibrated span Non-Volatile Memory: All programmed settings are stored in non-volatile memory for a minimum of ten years if power is lost. Recalibration: All ranges are calibrated at the factory. Recalibration is recommended at least every 12 months. Power Options: 85-265 VAC 50/60 Hz, 90-265 VDC, 20 W max or 12-24 VDC ± 10%, 15 W max. Powered over USB for configuration only.. Fuse: Required external fuse: UL Recognized, 5 A max, slow blow; up to 6 meters may share one 5 A fuse. Isolated Transmitter Power Supply: Terminals P+ & P-: 24 VDC ± 10%. 12-24 VDC powered skus selectable for 24, 10, or 5 VDC supply (internal P+/P- switch). 85-265 VAC skus rated @ 200 mA max, 12-24 VDC powered skus rated @ 100 mA max, @ 50 mA max for 5 or 10 VDC supply. Normal Rejection Mode:(PD6262) Greater than 60 dB at 50/60 Hz Isolation: 4 kV input/output-to-power line. 500 V input-to-output or output-to-P+ supply. Overvoltage Category: Installation Overvoltage Category II: Local level with smaller transient overvoltages than Installation Overvoltage Category III. Environmental:Operating Temperature Range: -40 to 65°C, Storage Temperature Range: -40 to 85°C, Relative Humidity: 0 to 90% non-condensing Connections: Removable screw terminal blocks accept 12 to 22 AWG wire, RJ45 for external relays, digital I/O, and serial communication adapters. Enclosure: 1/8 DIN, high impact plastic, UL 94V-0, color: black Mounting: 1/8 DIN panel cutout required: 3.622″ x 1.772″ (92 mm x 45 mm). Two panel mounting bracket assemblies are provided. Tightening Torque: Screw terminal connectors: 5 lb-in (0.56 Nm) Dimensions: 4.68″ x 2.45″ x 5.64″ (119 mm x 62 mm x 143 mm) (W x H x D) Weight: 9.5 oz (269 g) Warranty: 3 years parts & labor USB Connection: Compatibility: USB 2.0 Standard, Compliant Connector Type: Micro-B receptacle Cable: USB A Male to Micro-B Cable Driver: Windows 98/SE, ME, 2000, Server 2003/2008, XP 32/64-Bit, Vista 32/64-Bit, Windows 7 32/64-Bit, Windows 10 32/64-Bit Power: USB Port
Dual Input Functionality
Analog Inputs:(PD6262) Two non-isolated inputs, each separately field selectable: 0-20, 4-20 mA, ±10 V (0-5, 1-5, 0-10 V), Modbus PV (Slave) Pulse Inputs:(PD6363) Two, Field selectable: Pulse or square wave 0-5 V, 0-12 V, or 0-24 V @ 30 kHz; TTL; open collector 4.7 kΩ pull-up to 5 V @ 30 kHz; NPN or PNP transistor, switch contact 4.7Ω kpull-up to 5 V @ 40 Hz; Modbus PV (Slave) Channels: Channel A, Channel B, Channel C (Math channel) Programmable Constants: Constant P (Adder): -99.999 to 999.999, default: 0.000, Constant F (Factor): 0.001 to 999.999, default: 1.000Sequence of Operations for Input Programming: 1. Select Input for A and B 2. Set up the rate, total, and grand total engineering units for channels A & B, and units for math channel C 3. Set up rate, total, and grand total decimal points for channels A & B, and decimal point for math channel C 4. Program channel A & B rate parameters 5. Program channel A & B total and reset parameters 6. Set up the big and little displays and display intensity 7. Select the transfer function for A & B (e.g. Linear) 8. Select Math function for Channel C 9. Program constants for Factor (F) and Adder (P) 10. Program cutoff values for A and B Low Voltage Mag Pickup: (PD6363) Sensitivity: 40 mVp-p to 8Vp-p Minimum Input Frequency:(PD6363) 0.001 Hz Minimum frequency is dependent on high gate setting. Maximum Input Frequency:(PD6363) 30,000 Hz (10,000 for low voltage mag pickup) Accuracy:(PD6262) ±0.03% of calibrated span ±1 count, square root & programmable exponent accuracy range: 10-100% of calibrated span(PD6363) ±0.03% of calibrated span ±1 count Temperature Drift: 0.005% of calibrated span/°C max from 0 to 65°C ambient, 0.01% of calibrated span/°C max from -40 to 07°C ambient (PD6363) Rate display is not affected by changes in temperature. Signal Input Conditioning:(PD6262) Linear, square root, programmable exponent. Multi-Point Linearization: 2 to 32 points for channel A and B Programmable Exponent:(PD6262) 1.0001 to 2.9999 Low-Flow Cutoff: 0-999999 (0 disables cutoff function) Decimal Point: Up to five decimal places or none: d.ddddd, dd.dddd, ddd.ddd, dddd.dd, ddddd.d, or dddddd. Calibration Range (PD6262):
Input 1 & Input 2
An Error message will appear if input 1 and input 2 signals are too close together. Calibration Range (PD6363): Input 1 signal may be set anywhere in the range of the meter; input 2 signal may be set anywhere above or below the input 1 setting. Minimum input span between any two inputs is 10 Hz. An error message will appear if the input span is too small. Calibration: (PD6363) May be calibrated using K-factor, internal calibration, or by applying an external calibration signal. Input Impedance:(PD6262) Voltage ranges: greater than 500 K Ω. Current ranges: 50 – 100 Ω (depending on resettable fuse impedance). Input Overload:(PD6262) Current input protected by resettable fuse, 30 VDC max. Fuse resets automatically after fault is removed. HART Transparency:(PD6262) Analog input will not interfere with existing HART communications on the wired 4-20 mA signal K-Factor:(PD6363) Field programmable K-factor converts input pulses to rate in engineering units. May be programmed from 0.00001 to 999,999 pulses/unit. Filter:(PD6363) Programmable contact de-bounce filter: 40 to 999 Hz maximum input frequency allowed with low-speed filter.Time Base:(PD6363) Second, minute, hour, or day Gate:(PD6363) Low gate: 0.1-99.9 seconds, High gate: 2.0-999.9 seconds F4 Digital Input Contacts: 3.3 VDC on contact. Connect normally open contacts across F4 to COM. F4 Digital Input Logic Levels: Logic High: 3 to 5 VDC, Logic Low: 0 to 1.25 VDC
Rate Display Indication: 0 to 999999, lead zero blanking.Total Display & Total Overflow: 0 to 999,999; automatic lead zero blanking. Up to 999,999,999 with total-overflow feature. “oF” is displayed to the left of total overflow. Total Decimal Point: Up to five decimal places or none: d.ddddd, dd.dddd, ddd.ddd, dddd.dd, ddddd.d, or dddddd. Total decimal point is independent of rate decimal point. Channel A and B decimal points programmed independently. Dual Totalizer: Calculates total for channels A and B based on rate and field programmable multiplier to display the total in engineering units. Time base must be selected according to the time units in which the rate is displayed. Channel A and B totalizer parameters programmed independently. Totalizer Rollover: Totalizer rolls over when display exceeds 999,999,999. Relay status reflects the display value. Total Overflow Override: Program total A or B total reset for automatic with 0.1-second delay and set point 1 for 999,999 Totalizer Alarm Presets: Up to eight, user selectable under setup menu. Any setpoint can be assigned to channel A or B total or grand total (or C) and may be programmed anywhere in the range of the meter for total alarm indication. Total & Grand Total Reset: Via front panel button, external contact closure on digital inputs, automatically via user selectable preset value and time delay, or through serial communications. Channel A and B total and grand total reset parameters programmed independently. Total Reset Password: Total and grand total passwords may be entered to prevent resetting the total or grand total from the front panel. Non-Resettable Total: The grand totals can be programmed as non-resettable totals by entering the password “050873”. Both channels are set to non-resettable when this password is entered. Caution: Once the Grand Total has been programmed as “non-resettable” the feature cannot be disabled. Programmable Delay on Release: 0.1 and 999.9 seconds; applied to the first relay assigned to total or grand total. If the meter is programmed to reset total to zero automatically when the preset is reached, then a delay will occur before the total is reset.
Rating: 2 or 4 SPDT (Form C) internal and/or 4 SPST (Form A) external; rated 3 A @ 30 VDC and 125/250 VAC resistive load; 1/14 HP (≈ 50 W) @ 125/250 VAC for inductive loads Noise Suppression: Noise suppression is recommended for each relay contact switching inductive loads. Relay Assignment: Relays may be assigned to channel A or B rate, total, or grand total; channel C; or Modbus control. Deadband: 0-100% of span, user programmable High or Low Alarm: User may program any alarm for high or low trip point. Unused alarm LEDs and relays may be disabled (turned off). Relay Operation: automatic (non-latching), latching (requires manual acknowledge), sampling (based on time), pump alternation control (2 to 8 relays), off (disable unused relays), and manual on/off control mode. Relay Reset: User selectable via front panel buttons, digital inputs, or PC 1. Automatic reset only (non-latching), when input passes the reset point. 2. Automatic + manual reset at any time (non-latching). 3. Manual reset only, at any time (latching). 4. Manual reset only after alarm condition has cleared (latching). Note: Front panel button or digital input may be assigned to acknowledge relays programmed for manual reset. Time Delay: 0 to 999.9 seconds, on & off relay time delays. Programmable and independent for each relay. Fail-Safe Operation: Programmable and independent for each relay. Note: Relay coil is energized in non-alarm condition. In case of power failure, relay will go to alarm state. Auto Initialization: When power is applied to the meter, relays will reflect the state of the input to the meter.
Isolated 4-20 mA Transmitter Output
Output Source: Input channels A or B, rate, total, or grand total; channel C; max or min for channel A or B; highest or lowest max or min of A and B; set points 1-8; Modbus input; or manual control mode. Scaling Range: 1.000 to 23.000 mA for any display range Calibration: Factory calibrated: 4.000 to 20.000 = 4-20 mA output Analog Output Programming: 23.000 mA maximum for all parameters: Overrange, underrange, max, min, and break Accuracy: ±0.1% FS ±0.004 mA Temperature Drift: 0.4 µA/°C max from 0 to 65°C ambient, 0.8 µA/°C max from -40 to 0°C ambient Note: Analog output drift is separate from input drift. Isolated Transmitter Power Supply: Terminals I+ & R: 24 VDC ± 10%. Isolated from the input at >500 V. May be used to power the 4-20 mA output or other devices. All skus rated @ 40 mA max. External Loop Power Supply: 35 VDC maximum Output Loop Resistance:
35 VDC (external)
Protocol: Modbus® RTU Meter Address/Slave ID: 1 – 247 Baud Rate: 300 – 19,200 bps Transmit Time Delay: Programmable between 0 and 199 ms Data: 8 bit (1 start bit, 1 or 2 stop bits) Parity: Even, odd, or none with 1 or 2 stop bits Byte-to-Byte Timeout: 0.01 – 2.54 seconds Turn Around Delay: Less than 2 ms (fixed) Note: Refer to the ProVu Modbus Register Tables for details
Digital I/O Expansion Module
Channels: 4 digital inputs & 4 digital outputs per module System: Up to 2 modules for a total of 8 inputs & 8 outputs Digital Input Logic: High: 3 to 5 VDC Low: 0 to 1.25 VDC Digital Output Logic: High: 3.1 to 3.3 VDC Low: 0 to 0.4 VDC Source Current: 10 mA maximum Sink Current: 1.5 mA minimum +5 V Terminal: To be used as a pull-up for digital inputs only
4-Relay Expansion Module
Relays: Four Form A (SPST) rated 3 A @ 30 VDC and 125/250 VAC resistive load; 1/14 HP (≈ 50 watts) @ 125/250 VAC for inductive loads.
Dual Analog Output Expansion Module
Outputs: Two passive 4-20 mA analog outputs
Scaling Range: 3.000 to 23.000 mA for any display range
Differential Pressure Flow (PD6262)
The PD6262 can display flow rate and total by extracting the square root from the 4-20 mA signal from differential pressure transmitters. The user selectable low-flow cutoff feature gives a reading of zero when the flow rates drop below a user selectable value.
Display Flow Rate
User Selectable Low-Flow Cutoff
Only 2 Calibration Points Required
Weir Flow Calculated Using Exponential Signal Input Conditioning
Open Channel Flow (PD6262)
The PD6262, in combination with ultrasonic level transmitters, makes for an economical way to measure and display open channel flow rates and totals in most weirs and flumes, and take periodic samples. All the user needs to do is enter the exponents for the weirs or flumes into the PD6262 and the PD6262 automatically raises the input signals to those powers. Sampling can be based on the total flow or the flow rate. Each channel’s signal input conditioning is programmed independently.
Convert Pulse to 4-20 mA (PD6363)
The PD6363 accepts pulse outputs from flowmeters and with the appropriate option installed, can convert the pulses to a 4-20 mA signal. The 4-20 mA signal can be programmed to correspond to either the flow rate or the total flow.
Use K-Factor or Multi-Point Scaling
ProVu Powers the Flowmeter
Up to 3 Analog Outputs
Panel cutout required: 1.772″ x 3.622″ (45mm x 92mm)
Panel thickness: 0.040 – 0.250″ (1.0mm – 6.4mm)
Mounting brackets lock in place for easy mounting
Clearance: Allow 6″ (152 mm) behind the panel
MeterView® Pro Software
MeterView® Pro software is designed for use with ProVu, ProtEX-MAX, or Helios Series meters and allows users to remotely program, monitor, and datalog using a PC. Remote programming allows for all available meter settings to be programmed through an easy, user-friendly interface. The data acquisition feature allows the user to gather readings from a meter at user-selected intervals and generate charts using common tools like Microsoft® Excel. A linearization setup function is also included. With this utility the user can configure up to 32 linearization points and upload them to the meter. All configuration data can be saved to a file for future use. This software is accessible via the onboard USB connection on all Helios large display meters, ProVu panel meters, and ProVu-based ProtEX-MAX explosion-proof meters produced since 6 September 2016 (firmware version 4.0 or higher). In order for meters produced prior to 6 September 2016 (firmware version 3.1 or lower) to establish digital communications with a PC, a serial communications adapter is required. For an RS-232 connection, use a PDA1232 adapter. To determine the software version of a meter:
Go to the Diagnostics menu () and press Enter button.
Press Up arrow button and scroll to Information menu (Info).
Press Enter to access the software number (), version (), and serial number () information. Write down the information as it is displayed. Continue pressing Enter until all the information is displayed.
The meter returns to Run Mode after displaying all the settings.