Display: PD154; Four red LED channel indicators. PD158; Eight red LED channel indicators. One green LED power indicator. Alarm Messages: Custom printed clear adhesive labels. Area: PD154, 1.25″ x .60″ (32 mm x 15 mm), 4 messages PD158, 1.25″ x .25″ (32 mm x 6 mm), 8 messages User specified size and length, up to 4 lines (PD154) or 2 lines (PD158) of 14 characters of size 9 pt fonts. Programming Methods: Rear 4-position switch for sequence selection and horn operation. Three front panel pushbuttons for NO/NC input selection, sequence option, and action. Audible Alarm: 85 dB internal horn. Noise Filter: 40 ms debounce on inputs and external pushbuttons. Shared First-Out Systems: 1 ms unit-to-unit delay. Maximum of 200 units in the shared first-out system. Non-Volatile Memory: All programmed settings are stored in non-volatile memory for a minimum of ten years if power is lost. Power Options: 85-265 VAC, 50/60 Hz; 90-265 VDC, 20 W max; or 12-36 VDC, 12-24 VAC, 6 W max. Fuse: Required external fuse: UL Recognized, 5 A max, slow blow. Up to 6 annunciators may share one 5 A fuse Isolated Power Supply: 24 VDC ± 10% @ 200 mA max Standard on 85-265 VAC powered units only. Isolation: 4 kV input/output-to-power line. Overvoltage Category: Installation Overvoltage Category II: Local level with smaller transient overvoltages than Installation Overvoltage Category III. Environmental: Operating temperature range: -40 to 65°C. Storage temperature range: -40 to 85°C. Relative humidity: 0 to 90% non-condensing. Connections: Removable screw terminal blocks accept 12 to 22 AWG wire. Enclosure: 1/8 DIN, high impact plastic, UL 94V-0, front color: black Mounting: 1/8 DIN panel cutout required. Two-panel mounting brackets included. Tightening Torque: Screw terminal connectors: Gray: 4.5 lb-in (0.5 Nm). Green: 5 lb-in (0.5 Nm) Overall Dimensions: 4.68″ x 2.45″ x 4.19″ (62 mm x 119 mm x 106 mm) (H x W x D) Weight: 9.6 oz (272 g) UL File Number: E160849; 508 Industrial Control Equipment Warranty: 3 years parts & labor
Input Types: NO or NC switches: No external excitation required. Open collector transistor: Open circuit voltage approx. 3.3 VDC. Logic Levels: LOW = 0 to 0.9 VDC, HIGH = 2.4 to 28 VDC Update Rate: 41 ms following alarm state; 1 ms for alarm state clear. Sequences: Input follower, ISA Sequences A, F1A, F2A, F3A, M, F1M, and F3M per ISA Standard ISA-18.1-1979 R2004. Sequence Options: A, F1A, F2A, F3A, M, F1M, F2M, and input follower with selectable options -1 (silence pushbutton), -4 (no lock-in), and -6 (no horn) per ISA Standard ISA-18.1-1979 R2004
Rating: 2 SPDT (Form C); rated 3 A @ 30 VDC or 3A @ 250 VAC resistive load; 1/14 HP @ 125/250 VAC for inductive loads. Electrical Noise Suppression: A suppressor (snubber) should be connected to each relay contact switching inductive loads to prevent disruption to the microprocessor’s operation. Recommended suppressor value: 0.01 µF/470 Ω, 250 VAC (PDX6901). Relay Operation: Relay 1: Alarm state until the alarm is acknowledged. Relay 2: Alarm state if any channel indicating an alarm condition. Fail-Safe Operation: Programmable independent for each relay. Note: In fail-safe mode, the relay coil is energized in non-alarm condition. In case of power failure, the relay will go to the alarm state.
Level Monitoring with Level Switches
The Vigilante II is ideal for tank level switch monitoring.
Up to 8 Individually Labeled Level Switch Inputs
24 VDC Level Switch Power Supply
Relays for External Horns and Light Alarms
NEMA 4X Mounting Enclosures
Sunlight Readable Indication
Level Monitoring with Level Switches
First-Out Indication for Heating/Cooling Systems
Multiple Unit First-Out Indication
Remote Silence, Acknowledge and Reset
Internal 85 dB Horn,/li>
Fail-Safe Relays for Critical Applications
Connect PD765 Trident alarm relays to the Vigilante II for temperature alarm monitoring.
First-Out Alarm Indication
The Vigilante II can be programmed for multiple sequences with first-out alarm indication. This feature indicates the first point of failure of a system when multiple alarms occur.
Multiple Unit First-Out Alarm Indication
If multiple Vigilante II annunciators are connected for multiple unit first-out indications, only one input from all connected devices will display as a first-out alarm.